These 2 Pole 4 Wire Luminaire Ballast Disconnects enable fixture manufacturers and contractors to comply with the NEC 410.73 (G) & CEC 30-308(4) requirements for a means to safely disconnect non-residential flourescent fixtures while under load.
Our Luminaire ballast disconnects are simple to install - simply push tinned stranded or solid wires into wiring ports.
Low wire insertion force allows fast, easy connections.
Keyed Male/Female mating points provide touch proof disconnect under load
Orange "Safety" housing for ease of identification
Housing material: Nylon Thermoplastic, UL 94V-0 flame retardant
Electrolytic tin-plated internal copper bus for high conductivity
Current: 3A @120V
Working Temperature: (105°C)
Wire Range: 12-18 AWG Solid or stranded copper conductor